У вас є питання та ви шукаєте швидку відповідь? Шукайте серед питань, что часто задають.
In the Downloads section, present in the homepage.
All hoods with a 600m3/h motor require a 122mm diameter pipe.
All hoods with a motor ranging from 600m3/h to 1300m3/h require a 150mm diameter pipe or a 220x90mm ducting.
All hoods with a motor exceeding 1300m3/h require a 200mm diameter pipe.
Hoods must always be wider than your cooking hob:
- by about 10% for wall and island models;
- by 20-30% for ceiling models.
Wall and island hoods optimum distance is:
Ranging from 62 and 75cm with gas hobs.
52cm with induction hobs.
Maximum distance of ceiling hoods is of 150cm.
Ceiling, wall and island hoods with metallic filters in plain sight, larger than the hob and placed higher than usual (70cm from the hob).
Especially Virgola No-Drop, Professional collection and worktop models.
It's better to avoid sloped, glass hoods with perimetral suction.
For a step by step installation guide check out Falmec Youtube channel and Falmec website Support / Videoguides section!
No, you should order them separately, choosing the ones which are more suitable to your installing solution.
With induction hobs, because they just warm the pot and not the sorrounding area, causing an increase of condensation.
- Choose the right hood (dimension and power).
- Select the maximum suction speed.
- Turn on the hood before start cooking and program a late turn off.
- Use the lid pot.
- Don't use an excessive induction hob power.